IWE Grease and Fat Removal
In just one outlet a leading Grocery store have been encountering recurrent drainage issues as a direct consequence of an accumulation of fat, oils and also grease (FOG).
Industrial Water Equipment Ltd have been requested to help perform / do assessments making use of the IWE-Grease and Fat Removal Product to determine if the issue can be conquered. This Superstore had been dosing by hand powder bacterial solutions inside the Delicatessen, Butchers, Bakery and also the Staff members Eating area. It had been decided they would substitute the powdered products and use the IWE Grease and Fat Remover in the 4 sites. More over On top of that it had been decided to make use of the IWE Biological dosing fluid in to two dosing devices.
At the beginning of Oct closed locking units had been set up in the Restaurant. Within the Delicatessen as a result of small space, the lockable wall unit was established using a free-standing drum of IWE Grease and Fat Removal dosing fluid positioned underneath. This particular dosing fluid requires quarterly renewal.
Drain Quality once dosed with IWE Grease and Fat Removal
From the 2nd half of Dec, subsequent to 8 weeks of treatment solution using IWE Grease and Fat Remover, IWE initiated an assessment of the actual drainage outlines at the shop. All drainage pipes were found to be thoroughly clean as well as operating unhampered. A given was discovered within the wet well servicing the actual delicatessen. This particular well formerly ended up filling and actually overflowing accompanied by a bed smell. Employees now have reported there are zero smells. The actual well doesn’t fill up to overflowing. The edges are nice and clean. Just at higher level, over the existing highest load levels, is FOG deposit.
In the course of the assessment the higher level alarm system within the well had been continually sounding. This is because sulphonic acidity created by the actual decaying fat which had gathered round the alarm system probe/sensor had consumed the cabling from the probe/sensor. This issue won’t re-occur using powerful organic dosing on the drainpipes.
The drainpipes within the staff members kitchen area are actually now cleansed and also free running Even Having said that tough FOG is clear on the left of the kitchen area drain line. However this is remaining fat from the prior FOG accumulate prior to the treatment of IWE Grease and Fat Removal, and it’s outside the natural stream.
The client turned out to be over joyed with all the benefits provided from IWE Grease and Fat Remover.